Trans-Membrane Pressure (TMP) calculation for UF
Jun. 18, 2021
To calculate accurate Trans-Membrane Pressure (TMP), it is necessary to involve the height difference of inlet and outlet pressure gauges.Example calculation of TMP
TMP = (Pin - Hin) - (Pout + Hout)
= (70 - 10) - (20 + 25)
= 60 - 45
= 15 kPa
Note, the following formula may also be used:
TMP = Pin - Pout - total delta H
= 70 - 20 - (10 + 25) = 15 kPa
This Instruction Manual does not intend to guarantee the results of application of the information provided herein or the safety and the compatibility of this product.
Before using this product, the user is asked to check for its safety and compatibility with the intended purpose.
The content of this Instruction Manual is subject to revision from time to time.
Unauthorized use or reproduction of this manual is forbidden.
This content is extracted from “TORAY Pressurized PVDF Hollow Fiber Membrane Module “TORAYFIL™” Instruction Manual”(the Manual). Please refer to other contents stated in the Manual.